Stainless steel emergency rinse eyewash PP composite eyewash room
Nominal pressure Sealing pressure Working pressure Spray flow L/min Eyewash flow L/min Applicable conditions
0.4MPA 0.45MPA 0.20~0.40MPA ≥75.5 ≥11.4 Pure water at room temperature or water that meets sanitary standards
The selection of the main performance parameters is formulated with reference to the American ANSI Z358.1-2004 standard, taking into account the reduction of harmful substances to human skin and eye surface damage and irritation during the accident.
Structural characteristics of the emergency rinse eye wash room
1. Flushing system: The flushing nozzle is a stainless steel nozzle, which is used to rinse the whole body
2. Eyewash system: used to rinse eyes, face and other parts, the nozzle is equipped with an aerator, the water is soft, and there is a flow control valve between the two pipes of the double nozzle, which can adjust the flow rate by itself
3. Shower room: G11/4 water inlet is provided behind the middle, a water collection tank is provided in the lower part, and a G11/4 drainage outlet is provided behind the bottom of the box to prevent the outflow of sewage from eyewashing and spraying, and a lifting ring is installed under the side wall to facilitate loading and unloading transportation.
The main material of the emergency rinse eye washing room: high-quality stainless steel
How to use
The emergency rinse eye wash room door is a sliding folding door. If you need to wash your eyes, push the eyewash switch push plate clockwise, open the eyewash valve, pull back the pusher plate in the counterclockwise direction, and close the eyewash valve. When you need to flush, pull the shower switch handle down, the shower valve opens, push the shower switch handle upward, the shower valve is closed, and the eyewash switch push plate, dust cover and shower handle need to be reset after use.