Essential equipment for safety and labor protection. It is an emergency protection facility necessary for contact with acids, alkalis, organic matter and other toxic and corrosive substances. In the event of an accident, the degree of damage is minimized by rapid showering and rinsing.
Pressure rating MPa
Flow rate L/min
Normal temperature pure water or water that meets hygienic standards
The main performance parameters are selected to reduce the damage and irritation of harmful substances on human skin and ocular surface layer in the event of an accident.
1. The product model, certificate of conformity, instruction manual, and packing list must be re-examined before installation.
2. The installation location should be within 15 meters of the accident-prone location, and the flushing position can be reached within 10 seconds of running speed.
e. Install the eyewash section: Wrap the raw material tape at the thread of the eyewash nozzle and tighten it with the lower half of the reducer.
f. Install the double nozzle eye wash part: Put the G1⁄2” mesh mat into the G1⁄2” lock nut and connect it with the G1⁄2” connector
g. Connect the inlet pipe and drain pipe to check whether the ball valve switch is in place and there is no jamming.
h. In the middle of the two eyes of the double-head washing machine, the eye-washing flow regulating valve is used, and the flow rate of the eye-washing nozzle is controlled by the flow regulating valve. It has been debugged at the factory. However, due to the difference in water supply pressure and flow rate, it can be re-adjusted on site during installation to adjust the flow to the human eye. Adjustment method: Unscrew the top protective cap, use a flat-blade screwdriver to adjust the adjusting valve stem, rotate clockwise, and reduce the flow. Rotate counterclockwise and the flow rate increases.
1. This product is used in the environment above 0 °C. If it is used below 0 °C, it is necessary to carry out pipeline antifreeze maintenance;
2. Before installation, please rinse the water inlet pipe in advance;
3. It is recommended to install the water inlet control valve in the inlet pipe. After use, close the inlet control valve and close the eyewash valve after the water in the main body has been discharged.
Open the inlet control valve before use
1. When it is necessary to flush, please pull down the handle of the shower switch, the shower valve is opened (opening angle 90°), push the shower switch handle up, and the shower valve closes. (The ball valve connecting rod is closed at 45° above the ball valve and 45° at the lower side)
2. If you need to wash your eyes, please push the eyewash switch in a clockwise direction, the eyewash valve opens, pull the push plate counterclockwise, and the eyewash valve closes.
Small flushing water flow
Inlet pipe diameter is small, flow is not enough
Increase the inlet pipe 11⁄4 or 11⁄2
Eye wash nozzle has a small amount of water
a. Adjusting the valve stem to adjust the head
b. Flow regulating valve blocked
a. Rotate the lever counterclockwise
b. Flushing flow control valve
Eye wash nozzle has a large amount of water
Adjustment lever is not adjusted in place
Turn the control valve clockwise
Washing basin water
The drain hole in the eye wash basin is blocked or the sewer pipe is blocked
WJH0358 packing list
After unpacking, please check the number of accessories according to the following list to check whether there is any damage in transportation. If there is any problem or the quantity is insufficient, please contact our local distributor or the company immediately, and you will get a satisfactory answer.
Shower head section
Shower switch handle
Upper part of the riser (with the mother pad)
Eye wash double nozzle (with filter pad)
Wash basin part
Lower part of the riser (with lock mat)