This product can be used in field of Petroleum, Chemical, Laboratory, Medical Treatment etc., and flushing the chemistry liquid sputtered eye and face rapidly, so reduce the level of injury to the minimum.
Material: High density polyester, pro-environment and safety.
Capacity: The maximum reserve is 60L(16 gallon), workable is 40L availably, ensure flushing for 15 minute.
Water injection hole: wide water injection hole and apt to inject water, have dust cover.
Color: pro-environment green, aesthetic and striking.
Water flow: Due to change diameter on the water hole, so more bonhomie and rich, water yield is not lower than 1.5L/minute.
Located near happen accident place, see easily and usage conveniently. Can install wall or bracket, or can use with go-cart, mounting height is installation schematic diagram; when open the eye wash arm, the sprayer should be 83.8cm~114.3cm above ground.
B: if your choice washing fluid is purified water, should replace periodically (change period general is 5~7 days), every month must wash once at least( set drain valve, rotate the nut counterclockwise then drain water)
Suggest install indoor ,the environmental temperature is 2degree ~35 degree
b.water pipe or fitting clogging
1. a. Tank empty.Refill tank.
b.Obstruction in line or fitting.Clear obstruction.
2.Poor flow from eyewash head(s).
2. a. Tighten head assembly.
b.Check for obstructions. If necessary, remove eyewash head(s), clean and reassemble. To reassemble head, place cap screw through head and thread into head anchor two or three turns. Tilt head assembly and work anchor legs into eyewash armholes. Tighten assembly. Check for leaks.
3.Water leak between joints or fittings.
rubber tube ageing
3. a. Pull hose off fitting. Smooth raised plastic edge on center of fittings. Return hose and hose clamp to original position.
b. Tighten hose clamp(s) with pliers.