|material||National standard stainless steel (linkage flip type)|
|main body||304 stainless steel, the whole steel pipe is seamless steel pipe|
|water source||Room temperature domestic water in line with hygienic standards|
|sprinkler||The eyewash nozzle is equipped with a double-layer stainless steel filter screen, and the water is treated with a pressure buffer to form a foamy water column (it is automatically washed away by water when used, and it is not easy to lose)|
|Eye wash switch||When using, the lid of the eyewash basin needs to be opened, and clean water is automatically sprayed from the eyewash nozzle. After use, the lid of the eyewash basin is closed, and the eyewash switch is automatically turned off.|
|Start Time||1 second start||Production standards||American Standard ANSI Z358.1 2014|
|Nominal pressure||Inlet size||Outlet size||work pressure||eyewash flow|
|0.4 MPA||2/1 internal thread||1-1/4 female thread||0.2~0.4Mpa||≥11.4|
INSTALLATION AND DEBUGGING
|1. The product model, certificate of conformity, instruction manual and packing list must be re-inspected before installation.
2. The installation location should be within 15 meters from the accident-prone place, and the flushing place can be reached within 10 seconds at the running speed.
3. Assemble the parts as shown in the figure, and wrap the sealing tape (such as PTFE raw material tape) at the connection of each part, and connect the water pipes according to the diameter of the inlet and outlet respectively.
4. After connecting the inlet and drain pipes, check whether the ball valve switch is flexible and in place, and whether there is any jamming phenomenon.
METHOD OF USE
|Open the stainless steel dust cover by hand, and the water flow automatically flushes the dust cover of the eyewash elbow. (Double protection, health and safety) The central part of Niujiao Bay is equipped with a flow control valve, which can adjust the flow rate by itself, which is convenient and fast. After use, drop the stainless steel dust cover and turn off the water supply.|
|1. Comprehensive inspection should be carried out more than once a week to test the reliability and effectiveness of the device, so as to ensure the emergency and effective use in the event of an accident, and to provide personal safety and health protection.
2. This product is not a device, it only plays the role of emergency flushing and reducing the damage of harmful substances to the human body. 3. In the event of an accident, the victim must choose the flushing time according to the intrusion procedure of harmful substances. Prepare emergency rescue measures during the period.