Installation and commissioning:
1. The product model, certificate, instruction manual and packing list must be re-examined before installation.
2. The installation position should be within 15 meters from the accident-prone area, and the flushing position can be reached within 10 seconds of running speed.
3. Installation and commissioning:
a. The base is connected to the lower half of the riser: the raw material belt is wound at the base thread and the water outlet is connected tightly.
b. Install the base: adjust the direction of the three-way drain according to the position of the drain pipe, draw the punching position according to the screw hole of the base, and then set the M10 expansion screw or anchor bolt according to the ground level.
c. Install the shower pipe: screw the shower head to the elbow of the nozzle pipe, and then wrap the raw tape at the other end of the nozzle pipe, connect it with the upper part, adjust the position, and lock with the locking nut. .
d. Connect the upper half and the lower half: put the cushion by the mother, and tighten it by the mother.
e. Install the eye wash basin part: wrap the raw material tape at the thread of the eye wash nozzle, and screw it tightly with the lower half of the reducer;
f. Install the double-head part of the eye wash: Put the G1⁄2″ mesh pad in the lock nut and tighten the connection with the G1⁄2″.
g. Connect the inlet pipe and drain pipe, test the push plate, insert the push plate into the valve stem of the eye wash valve, push the push plate counterclockwise to make the valve in the closed position, remove the push plate, and reinstall the direction of the push plate. The front side of the push plate is vertically upward and repeatedly opened to check whether the valve switch is flexible and in place, and there is no jamming phenomenon.
1. This product is used in the environment above 0 °C. If it is used below 0 °C, it is necessary to carry out pipeline antifreeze maintenance;
2. Before installation, please rinse the water inlet pipe in advance;
3. It is recommended to install the water inlet control valve in the inlet pipe. After use, close the inlet control valve and close the eyewash valve after the water in the main body has been discharged.
Open the inlet control valve before use
1. When it is necessary to shower, please pull down the handle of the shower switch, the shower valve is opened (opening angle 90°), push the shower switch handle up, the shower valve is closed (the ball valve connecting rod is closed at 45° above the ball valve, 45° below is on).
2. If you need to wash your eyes, please push the eyewash switch in a clockwise direction, the eyewash valve opens, pull the push plate counterclockwise, and the eyewash valve closes. The dust cover should be reset after use.
1. Only allow emergency use when an accident occurs. It is strictly forbidden to use the bathing method in order to avoid product failure and lead to undue accidents.
2. More than one comprehensive test should be conducted every week to verify the reliability and effectiveness of the device to ensure emergency and effective use when the accident occurs. This product is not a medical device, it only serves as an emergency shower and reduces the damage of harmful substances to the human body.
3. In the event of an accident, the victim must select the shower time based on the degree of damage of the hazardous substance. Prepare emergency rescue measures during the period.